Grounding screw terminal
Split-circuit receptacle is attached to a black hot wire, a red hot wire, a white neutral wire, and a bare grounding wire The wiring is similar to a switch-controlled receptacle
The hot wires are attached to the brass screw terminals. and the connecting tab or tin between the brass terminals is removed. The white wire is attached to a silver screw terminal, and the connecting tab on the neutral side remains intact The grounding wire is pig-tailed to the grounding screw terminal of the receptacle and to the grounding screw attached to the box.
Two-slot receptacle is often found in older homes. The black hot wires are connected to the brass screw terminals. and the white neutral wires are pigtailed to a silver screw terminal
Two-slot receptacles may be replaced with three-slot types, but only if a means of grounding exists at the receptacle box
Black hot wires
Silver screw terminal
Brass screw terminal
Two cables entering the box indicates middle-ot-run wiring
Was this article helpful?
Wonder No Longer About Things Like Designs, Tools And Safety. These Problems Among Others Will Be Covered In This E-Book. You Will Be Creating Great Wooden Works Of Art In Very Little Time At All! For The Beginning Woodworker, The Construction of Handcrafted Wood Creations Can Be a Daunting And Overwhelming Experience. Well, Not Anymore!